SECTION III: PREVENTlVE MAINTENANCE CHECKS AND SERVICES [PMCS]
Clean and lubricate cable (refer to TM 9-2350-256-10).
Clean and lubricate cable (see Appendix J).
Clean and lubricate stayline cable in accordance with
b. Inspect boom yoke/pulley cotter pins. Replace if
damaged or missing (see paragraph 11-11).
W A R N I N G
The unit commander or senior officer in charge
of maintenance personnel assigned to remove
and dispose of contaminated gas filters must
prescribe necessary protective clothing to be
worn during this operation. They must also
prescribe necessary safety measures to be
followed including the decontamination
operation that must be performed before new
gas filters are installed in housing assembly
(refer to TM 3-220).
Check that air flow is 3.0 to 4.5 standard cubic feet/minute
(scf/m) or 2.1 to -1.5 inch water gage (IWG) at each station
using the M39 Tester (Appendis B, item 160).